Find the documents you need for your ground mount installation below in addition to some Frequently Asked Questions. If you’re unable to find what you’re looking for please contact us right away, and we’d be more than happy to help.
2” Schedule 40 steel pipe is generally used for smaller arrays, such as residential applications, because it’s lightweight and easy to handle. 3” Schedule 40 steel pipe is most useful for larger arrays, where the longer E-W span helps reduce the number of concrete foundations. But, 3” Schedule 40 steel pipe is also heavier and sometimes requires heavy machinery for installation. Before purchasing your pipes, confirm the specifications with the Parts Catalog.
IronRidge provides standard foundation sizes for various soil classes. However, some soils may be extremely difficult to dig into, such as granite or rocky soils. Solutions for these soil types include epoxying rebar into the granite and pouring the foundations above the ground, connecting the piers with low depth grade beams, or casting the piers into above ground ballast blocks. Consult an engineer for structural review if using a foundation design other than those described in the IronRidge Certification Letters.
North to South pier dimensions are static measurements in our Ground Mount design that are either 7.5’ or 9’, depending on the number of modules per column. Refer to the assembly drawing found at the bottom of the IronRidge Certification Letter for dimension details. The certification letters can be found in the Documents & Resources section under the Ground-based tab on the IronRidge website.
The maximum “above ground length” for the southern vertical piers is 2’6”. To prevent exceeding this length on either side of the array, break the array into segments. This “stepped” array will prevent the East or West side of the array from being too high. If this is not a viable option, consult an engineer for alternative approaches.
Many installers create a temporary set of “forms” to suspend the East to West cross pipes, with the vertical pipes already attached to them. This approach allows you to assemble and level your sub-structure at the appropriate height, then pour all of the concrete at once. Always refer to the Ground Mount Installation Manual prior to assembly.